This European Standard specifies the common requirements and test methods, as well as the classification, marking and energy labelling of gas-fired central heating boilers that are fitted with atmospheric burners, fan assisted atmospheric burners or fully premixed burners, and are hereafter referred to as “boilers”.
This European Standard is to be used in conjunction with the specific Parts 2 (Part 2-1 and following ones).
This European Standard applies to boilers of types B and C.
NOTE For further background information on appliance types see CEN/TR 1749:2014 .
a) that use one or more combustible gases of the three gas families at the pressures stated in EN 437;
b) where the temperature of the water is below or above 105 °C during normal operation;
c) where the maximum operating pressure in the water circuit does not exceed 6 bar;
d) which can give rise to condensation under certain circumstances;
e) which are declared in the instructions for installation to be either a "condensing" boiler or a "low temperature boiler" or a "standard boiler" or an "other boiler". If no declaration is given the boiler is to be considered both a "standard boiler" and an "other boiler";
NOTE The Ecodesign Directive defines "other boilers", "low temperature boilers" and "condensing boilers". The Boiler Efficiency Directive defines "standard boilers", "low temperature boilers" and "condensing boilers". Depending on the legislation applied, a boiler can be both "a standard boiler" and an "other boiler"."
f) which are intended to be installed inside a building or in a partially protected place;
g) which are intended to produce also hot water either by the instantaneous or storage principle as a single unit.
This European Standard applies to boilers designed for sealed water systems or for open water systems.
NOTE This general standard and the specific standards (see Part 2) provide requirements for boilers with known constructions. For boilers with any alternative constructions, which might not fully be covered by this standard or a specific standard, the risk associated with this alternative construction will need to be assessed.
An example of an assessment methodology, based upon risk assessment, is given in Clause 11.
This European Standard is not intended to cover appliances intended for connection to gas grids where the quality of the distributed gas is likely to vary to a large extent over the lifetime of the appliance (see Annex EE).
This European Standard is not intended to cover appliances designed and constructed to burn gas containing toxic components.
When the standard is harmonized under a directive or regulation, the word Harmonized appear. When such an inscription does not appear, it means that the standard is related to / supporting the relevant directive or regulation.
Commission Delegated Regulation (EU) No 811/2013 of 18 February 2013 supplementing Directive 2010/30/EU of the European Parliament and of the Council with regard to the energy labelling of space heaters, combination heaters, packages of space heater, temperature control and solar device and packages of combination heater, temperature control and solar device
Commission Regulation (EU) No 813/2013 of 2 August 2013 implementing Directive 2009/125/EC of the European Parliament and of the Council with regard to ecodesign requirements for space heaters and combination heaters
REGULATION (EU) 2016/426 OF THE EUROPEAN PARLIAMENT AND OF THE COUNCIL of 9 March 2016 on appliances burning gaseous fuels and repealing Directive 2009/142/EC